WHOLE HOUSE WATER SOFTENERS WITH ELECTRONIC VALVE METER
The typical water softener is a mechanical appliance that's plumbed into your home's water supply system. All water softeners use the same operating principle: They trade the minerals for something else, in most cases sodium. The process is called ion exchange.
The heart of a water softener is a mineral tank. It's filled with small polystyrene beads, also known as resin or zeolite. The beads carry a negative charge. Calcium and magnesium in water both carry positive charges. This means that these minerals will cling to the beads as the hard water passes through the mineral tank. Sodium ions also have positive charges, albeit not as strong as the charge on the calcium and magnesium. In the traditional water softeners, when a very strong brine solution is flushed through a tank that has beads already saturated with calcium and magnesium, the sheer volume of the sodium ions is enough to drive the calcium and magnesium ions off the beads. Water softeners have a separate brine tank that uses common salt to create this brine solution.
In normal operation, hard water moves into the mineral tank and the calcium and magnesium ions move to the beads, replacing sodium ions. The sodium ions go into the water. Once the beads are saturated with calcium and magnesium, the unit enters a 3-phase regenerating cycle. First, the backwash phase reverses water flow to flush dirt out of the tank. In the recharge phase, the concentrated sodium-rich salt solution is carried from the brine tank through the mineral tank. The sodium collects on the beads, replacing the calcium and magnesium, which go down the drain. Once this phase is over, the mineral tank is flushed of excess brine and the brine tank is refilled
Sizing Your Softener:
Water hardness can be reported in "grains per gallon" (gpg), "parts per million" (ppm) or "milligrams per liter" (mg/l). Most of the industry calculates softener size using gpg. You can divide ppm and mg/l by 17.1 to obtain your hardness value in grains per gallon.
You will also need to account for the iron and manganese in your water, and a quick way to get this value is to multiply your iron and manganese concentration (in ppm or mg/l) by a factor of 4. Add this number to the hardness value you determined above. The resulting total value is similar to a "compensated" hardness value, and will better serve to size your softener.
In the example below we will use 4 people in the home and a hardness value of 10 grains per gallon, and iron concentration of 2 ppm.
Multiply 4 people in the home x 75 gallons water usage per person per day x (10 grains hardness + (2 ppm iron x 4)) = 5,400 grains of hardness to be removed per day. So with a 32,000 grain system, set capacity would be about 26,000 grains (20% lower than actual - reserve capacity), and a metered unit would regenerate approximately every 5 days (26,000 divided by 5,400), which is acceptable.
Use the formula above to adjust for the number of people actually living in your home, and your specific water hardness.
With normal to low levels of iron in your water, you can size your softener to regenerate between every 5 to 10 days. With higher levels of iron (5 mg/l and higher) and manganese (1 mg/l and higher), it's better to size a system to regenerate more frequently, in order to keep the resin bed free of accumulated deposits. In this case, a regeneration every three to five days may be required. If you have very high iron levels in your water, please contact us by email or telephone for a sizing recommendation.
ELECTRONIC METERED SOFTENING WATER SYSTEMS.
THIS IS SYSTEMS IS GOOD FOR 1-3 PERSONs. WITH HIGH HARDNESS .
This systems includes:
ELECTRONIC metered valve
mineral Tank 9 X 48" could be any color.
18 x 33 Brine tank
24 V Transformer IF NEEDED
Distributor assembly w/ upper and lower Screens.
SHIPPING TO 48 US STATES ONLY
- Additional Information
Model Number WHS948SXT UPC No Brand Premier Water Systems Item Number 20 Shipping Length 0 Shipping Width 0 Shipping Height 0 Shipping Weight 0
Customer Reviews 1 item(s)
- Great value and service
Wanted to wait awhile before posting a review to get some run time on the Water softener. I bought this unit to replace a previous Sears softener after the resin trap blew out in it and clogged all my house plumbing. Now that the Softener has been in service for several months, I really have no complaints about this unit. I self installed - the instructions were clear and detailed. No installation issues at all with the unit itself. Other than connecting piping and salt, everything required was included. One thing I did do was add in/out isolation valves and filters this time - never want to go through another resin bed failure again! The controller works great, and the resin tank is well built. The salt reservoir is a little flimsy, but good enough. At this price point, it represents a major savings over other big box hardware store or dealer installed options, and it has worked flawlessly since installation. Being able to fine tune the unit to my specific water hardness and usage makes it pretty miserly with salt consumption. I would definitely recommend this to others.